Published: May 16, 2022
Digital input period measurement feature reports inaccurate value
Firmware for the following modules:
Resolved In Version:
While using a digital input configured for period measurement (for example, Period (One-Time) in groov Manage or Period in PAC Control), the period measurement value may be inaccurate and is low by 37.5%.
Since the value is always reported low, multiply the period measurement by 1.6 to correct the value.
Opto 22 has resolved this issue.
Contact: Opto 22 Product Support.
Phone: 800-835-6786 or 951-695-3080
This Opto 22 Knowledge Base ('OptoKB') article is intended to provide general technical information on a particular subject or subjects and is not an exhaustive treatment of such subjects. Accordingly, the information in this OptoKB article is not intended to constitute application, design, software, or other professional engineering advice or services. Opto 22 may modify the OptoKB articles at any time. Before making any decision or taking any action which might affect your equipment, you should consult a qualified professional.
OPTO 22 DOES NOT WARRANT THE COMPLETENESS, TIMELINESS, OR ACCURACY OF THE DATA CONTAINED IN THIS OPTOKB ARTICLE AND MAY MAKE CHANGES THERETO AT ANY TIME AT ITS SOLE DISCRETION WITHOUT NOTICE. FURTHER, ALL INFORMATION CONVEYED HEREBY IS PROVIDED TO USERS 'AS IS.' IN NO EVENT SHALL OPTO 22 BE LIABLE FOR ANY DAMAGES OF ANY KIND INCLUDING DIRECT, INDIRECT INCIDENTAL, CONSEQUENTIAL, LOSS PROFIT, OR DAMAGE, EVEN IF OPTO 22 HAS BEEN ADVISED ON THE POSSIBILITY OF SUCH DAMAGES.
OPTO 22 DISCLAIMS ALL WARRANTIES WHETHER EXPRESSED OR IMPLIED WITH RESPECT TO THE INFORMATION (INCLUDING HARDWARE, SOFTWARE, AND/OR FIRMWARE) PROVIDED HEREBY, INCLUDING THE IMPLIED WARRANTIES OF FITNESS FOR A PARTICULAR PURPOSE, MERCHANTIBILITY, AND NON-INFRINGEMENT. Note that certain jurisdictions do not sanction the exclusion of implied warranties: thus, this disclaimer may not apply to you.
Copyright © 2023 Opto 22. All rights reserved.