Published: March 30, 2022
Scaling values for analog channels may not be correct
Firmware for the following groov EPICs:
Firmware for the following groov
For groov EPICs: All versions
For groov RIOs: All versions prior to 3.3.1
Resolved In Version:
For groov RIOs: 3.3.1
If you set the scaling values for an analog channel such that the new high scale value matches the current low scale value or the new low scale value matches the current high scale value, then one of the scaling values will be set to the default value, as follows:
- If you set the scaling values through a PAC Control strategy or CODESYS application, then the high scale value is set to the default.
- If you set the scaling values through groov Manage, then low scale value is set to the default.
- After PAC Control or CODESYS configures the I/O, use groov Manage to manually set the desired values for the high or low scale.
- If you want to adjust the I/O channel's current default scaling,
- To set a high scale value that matches the current low scale value, set the scaled value to just below or above the desired value.
- To set a low scale value that matches the current high scale value, set the scale value to just over or below the desired value.
For example, a 4–20 mA channel has a default scaling of 20.0 mA for high and 4.0 mA for low. If you want to set the high scale value to 4.0 and the low scale value to 0.0, then use 3.99999 or 4.00001 for the high scale.
Opto 22 has resolved this issue and will include the fix in an upcoming release.
Contact: Opto 22 Product Support.
Phone: 800-835-6786 or 951-695-3080
This Opto 22 Knowledge Base ('OptoKB') article is intended to provide general technical information on a particular subject or subjects and is not an exhaustive treatment of such subjects. Accordingly, the information in this OptoKB article is not intended to constitute application, design, software, or other professional engineering advice or services. Opto 22 may modify the OptoKB articles at any time. Before making any decision or taking any action which might affect your equipment, you should consult a qualified professional.
OPTO 22 DOES NOT WARRANT THE COMPLETENESS, TIMELINESS, OR ACCURACY OF THE DATA CONTAINED IN THIS OPTOKB ARTICLE AND MAY MAKE CHANGES THERETO AT ANY TIME AT ITS SOLE DISCRETION WITHOUT NOTICE. FURTHER, ALL INFORMATION CONVEYED HEREBY IS PROVIDED TO USERS 'AS IS.' IN NO EVENT SHALL OPTO 22 BE LIABLE FOR ANY DAMAGES OF ANY KIND INCLUDING DIRECT, INDIRECT INCIDENTAL, CONSEQUENTIAL, LOSS PROFIT, OR DAMAGE, EVEN IF OPTO 22 HAS BEEN ADVISED ON THE POSSIBILITY OF SUCH DAMAGES.
OPTO 22 DISCLAIMS ALL WARRANTIES WHETHER EXPRESSED OR IMPLIED WITH RESPECT TO THE INFORMATION (INCLUDING HARDWARE, SOFTWARE, AND/OR FIRMWARE) PROVIDED HEREBY, INCLUDING THE IMPLIED WARRANTIES OF FITNESS FOR A PARTICULAR PURPOSE, MERCHANTIBILITY, AND NON-INFRINGEMENT. Note that certain jurisdictions do not sanction the exclusion of implied warranties: thus, this disclaimer may not apply to you.
Copyright © 2023 Opto 22. All rights reserved.