Published: August 20, 2019
groov analog input values may read low after restarting GRV-EPIC-PR1
Firmware for GRV-EPIC-PR1
All versions prior to 1.4.0
Resolved In Version:
Analog input values may read low after restarting GRV-EPIC-PR1. This is caused by the gain parameter for the analog input inadvertently being set to 0.8999, instead of 1.0. This can happen after restarting GRV-EPIC-PR1 if the following steps have occurred:
- You do a Reset I/O to Defaults operation on your GRV-EPIC-PR1.
- In PAC Control, you download a strategy with the option set to store the strategy to flash and with the analog input channel configured to not send values for Offset and Gain. (In PAC Control, when you edit or add an analog point, the "Send Values" checkbox for Offset and Gain is not checked.)
These symptoms are similar to those described in KB87693
; however, the cause is different.
The correct default values for offset and gain are 0 and 1.
Do one of the following:
- From within PAC Control, edit all analog input channels so you can check the "Send Values" checkbox for Offset and Gain and use the correct default values (0 and 1, respectively).
- After a PAC Control strategy is downloaded, go to groov Manage, navigate to the configuration page for all analog input channels (Home > I/O > analog_module > channel > Configure), ensure that offset and gain are configured correctly (0 and 1, respectively), then click "Save".
After either procedure, the values will properly persist in flash.
Opto 22 has resolved this issue.
Contact: Opto 22 Product Support.
Phone: 800-835-6786 or 951-695-3080
This Opto 22 Knowledge Base ('OptoKB') article is intended to provide general technical information on a particular subject or subjects and is not an exhaustive treatment of such subjects. Accordingly, the information in this OptoKB article is not intended to constitute application, design, software, or other professional engineering advice or services. Opto 22 may modify the OptoKB articles at any time. Before making any decision or taking any action which might affect your equipment, you should consult a qualified professional.
OPTO 22 DOES NOT WARRANT THE COMPLETENESS, TIMELINESS, OR ACCURACY OF THE DATA CONTAINED IN THIS OPTOKB ARTICLE AND MAY MAKE CHANGES THERETO AT ANY TIME AT ITS SOLE DISCRETION WITHOUT NOTICE. FURTHER, ALL INFORMATION CONVEYED HEREBY IS PROVIDED TO USERS 'AS IS.' IN NO EVENT SHALL OPTO 22 BE LIABLE FOR ANY DAMAGES OF ANY KIND INCLUDING DIRECT, INDIRECT INCIDENTAL, CONSEQUENTIAL, LOSS PROFIT, OR DAMAGE, EVEN IF OPTO 22 HAS BEEN ADVISED ON THE POSSIBILITY OF SUCH DAMAGES.
OPTO 22 DISCLAIMS ALL WARRANTIES WHETHER EXPRESSED OR IMPLIED WITH RESPECT TO THE INFORMATION (INCLUDING HARDWARE, SOFTWARE, AND/OR FIRMWARE) PROVIDED HEREBY, INCLUDING THE IMPLIED WARRANTIES OF FITNESS FOR A PARTICULAR PURPOSE, MERCHANTIBILITY, AND NON-INFRINGEMENT. Note that certain jurisdictions do not sanction the exclusion of implied warranties: thus, this disclaimer may not apply to you.
Copyright © 2023 Opto 22. All rights reserved.